The scope of supply includes a frame in Q-Design QRR1, an attachment frame, a battery
mounting plate and an adhesive foil. For mounting in frames with 55- or 63-neckline (without
batteries!) also an intermediate frame ZR and ZRF in the same color and a mounting plate.
In the as-delivered condition, the energy storage is empty and needs to be charged before use.
Either via the red/black 12V DC power cable for about 5 minutes or via the solar cell in broad
daylight for about 5 hours or from 13/2013 by inserting two pieces AAA batteries (not included in
delivery) for about 5 minutes.
In normal operation, the power supply is either through the cable with a 12V DC power supply
unit FSNT61-12V/6W in a flush-mounted box under the sensor or from 13/2013 with AAA
batteries, supported by the solar cell, or only with the solar cell under normal ambient light, in a
daily average of at least 200lux. If only the solar cell is available, the energy storage must first be
charged for several days with daylight.
If the connecting cable is not needed, it can be cut off. This means the sensor requires no
installation depth behind the mounting plate. It can be screwed or affixed to any flat surface.
An adhesive foil is supplied.
We recommend sheet metal countersunk screws 2.9x25mm, DIN 7982 C, for screw connections.
Both with rawl plugs 5x25mm and with 55mm switch boxes. See chapter Z: 'Accessories'.
The complete module can be removed from the frame so that it can be screwed on.
The sensor sends a message every 100 seconds to the Eltako wireless network at an actual
temperature change of minimum 0.3°C. The bistable display is updated.
If there is no change, a status report is sent every 20 minutes.
Measurement accuracy is approx. 1°C